central air malfunction?
sometime the condenser goes on and the system is on but the blower does not work.
i hit power on n off a few times and the blower kicks in.
the blower that blows air in to the duct work
- Spock (rhp)Lv 71 month ago
you're talking about the internal circulation blower, I assume. There are several reasons why this might stop working, and the most common is that the run/start capacitor needs to be replaced. that's inside the air handler [the indoor unit] and if you don't have a handyman who can test and replace it, the a/c guy will do so for about $100 plus parts. Be sure to give them the exact brand and model number [from the number plate on the indoor unit] and a full description of the problem so they can look up and send the correct capacitor out with the technician. -- Grampa [other causes exist and aren't so simple ... and you'll need the technician to find and fix them]
- Anonymous1 month ago
Replace the blower capacitor.